1. U0/U: 0.6/1kV
2. Standard: IEC60502, BS7870, GB/T12706
3. Max. working temperature: 90 °C , can be 110 °C as requirement
4. Conductor: Class 1/2 annealed bare copper/aluminum solid or strands
5. Insulation: XLPE/PVC
6. Armored: STA
7. Sheath: PVC
8. Cross section area: 1.5~630mm2
9. Cores: 1~5 cores,3C+1E,4C+1E,3C+2E
10. Packing:Wooden drum or as requirement
11. Certification : ISO9001/ISO14001/OHSAS18001/CCC/CE/CB
12. Remark: Flame retardant,fire resistance,low smoking and Halogen free,or other property can be avaliable
|Type||Desciption||Rated Voltage||NO. of Cores||Nomibal section(mm2)||Applications|
|YJV YJLV||Cu or Al conductor,XLPE insulated.PVC sheathed electric cable||0.6/1KV||1,2,3,4||1.5 to 400||For laying indoors and outdoors.The LV XLPE insulated power cable is used in transmission and distribution system at rated voltagae U(Um) ≤10KV.The HV XLPE insulated power cable refers to the power cable transmission between 10KV-35KV, it is often applied to the main road of power transmission. Able to bear certain traction during installation, but not external mechanical forces.|
|3+1||3×4+1×2.5 to 3×400+1×185|
|6/6kV||1,3||25 to 500|
|8.7/10kV 8.7/15kV 12/20kV||1||25 to 500|
|3||25 to 300|
|21/35kv||1||50 to 500|
|YJV22 YJLV22||Cu or Al conductor,XLPE insulated steel tape armoured PVC sheathed electric cable||0.6/1KV||3||1.5 to 400||Suitable for burying in ground, Able to bear external mechanical forces but large pulling forces.|
|4||4 to 240|
|6/6kV 8.7/10kV 8.7/15kV 12/20kV||3||25 to 300|
|21/35kv||3||50 to 240|
STA Armored Electric Cable YJV22 4+1 Core Cable applies to electrical power transmission and distribution lines with AC rated voltage Uo/ U up to and including 0.6/1kV.
For outdoor and indoor installation in damp and wet locations,laid directly in the ground where excessive mechanical stresses are present in sloping and moving terrains and in vertical or inclined laying,as well as in locations susceptible to sliding.
|Cu Core||Al Core|
|VV(VY);PVC(PE)sheathed power cable||VLV(VLY);PVC(PE)sheathed power cable|
|VV22(VV23);steel tape armoured,PVC(PE)sheathed power cable||VLV22(VLV23);steel tape armoured,PVC(PE)sheathed power cable|
|VV32(VV33),VV42(VV43);steel wire armoured ,PVC(PE)sheathed power cable||VLV32(VLV33),VLV42(VLV43);steel wire armoured ,PVC(PE)sheathed power cable|
Rated voltage: 0.6 / 1 kV
Maximum Conductor Temperature: under normal (90 OC), emergency (130OC) or short circuit no more than 5 s (250℃) conditions.
Min. Ambient Temp. 0 OC, after installation and only when cable is in a fixed position
Min. Bending Radius: 12 x cable O.D
|Nom. Cross-section of conductor||Strands No./Dia. Of Conductor||Insulation Thickness||Inner Covering Thickness||Steel Tape Thickness||Sheath Thickness||Approx. O.D.||
|Max. D.C Resistance of Conductor (20 ℃)||Testing Voltage A.C||Current Rating|
|mm2||pc/mm||mm||mm||mm||mm||(mm)||kg/km||Ω /km||kV/5min||In air (A)||In soil(A)|
|2 × 4||1/2.25||0.7||1.2||2 × 0.2||1.8||15.0||433||4.61||3.5||34||45|
|2 × 6||1/2.76||0.7||1.2||2 × 0.2||1.8||16.0||500||3.08||3.5||43||57|
|2 × 10||7/1.38||0.7||1.4||2 × 0.2||1.8||19.0||673||1.83||3.5||60||77|
|2 × 16||7/1.78||0.7||1.4||2 × 0.2||1.8||21.0||857||1.15||3.5||83||105|
|2 × 25||7/2.14||0.9||1.6||2 × 0.2||1.8||24.0||1173||0.727||3.5||105||125|
|2 × 35||7/2.52||0.9||1.6||2 × 0.2||1.8||26.0||1449||0.524||3.5||125||155|
|2 × 50||10/2.52||1.0||1.8||2 × 0.2||1.8||25.0||1877||0.387||3.5||160||185|
|2 × 70||14/2.52||1.1||1.8||2 × 0.2||1.8||27.0||2454||0.268||3.5||200||225|
|2 × 95||19/2.52||1.1||2.0||2 × 0.2||1.9||30.0||2483||0.193||3.5||245||270|
|2 × 120||24/2.52||1.2||2.0||2 × 0.2||2.0||33.0||4213||0.153||3.5||285||310|
|2 × 150||30/2.52||1.4||2.0||2 × 0.5||2.0||38.0||5087||0.124||3.5||325||345|
International: IEC 60502, IEC 60228, IEC 60332
China: GB/T 12706.1-2008
Other standards such as BS,DIN and ICEA upon requestfont-size:10.0000pt;mso-font-kerning:0.0000pt;" >PVC type ST2 to IEC 60502, black
All cable For exporting are well packed and protected by wooden drum or Wood and Steel Drum.
The packing material is depended on the weight and size of cable.
The good information, manufacture information, and the client's information is firmly printed on each size of drum.
After the well packed cable drums sent to Sea Port, they are loaded into 20 FT container or 40 FT container. All cable drum are firmly fixed by safety belt to make sure, no movement during the sea freight.
The size of the container is chosed according to weight of total loaded goods or as per the client's requirement.