Single Core 3.8/6.6-19/33KV Copper /Aluminium Armoured Electrical Cable 1Cx50SQMM to 1Cx 1000SQMM
High Tension Armoured Power Cable Power Cable
|Conductor:||Cu round aluminum, multi wire stranded compacted (RM), class 2 acc. to HRN HD 383 / IEC 60228 / DIN VDE 0295|
|Inner screen:||extruded semi-conductive skin on conductor|
|Insulation:||XLPE (cross-linked polyethylene, recent mark: PE-X) compound DIX 8 acc. to HRN HD 620 S1 ili 2XI1 acc. to DIN VDE 0207 dio 22|
|External screen:||extruded semi-conductive skin on insulation, longitudinally spliced with insulation (+tape of semi-conductive material)|
|Conductorscreen:||copper tape wrapped in counter-helix|
|Filler:||fillers strip, yarn, or paper|
|Wrapping:||non woven wrapping tape or flame retardant or water proof|
|Inner covering:||Extruded PVC|
|Overall Sheath||polyvinylchloride (PVC) or FR-PVC, PE, LSOH|
|Sheath color||Black, red or customized|
a. Used in transformer stations, switching blocks, in electric power plants and industrial plants. Medium voltage power cable for static application in ground, within and outside facilities, outdoor, in cable canals, in water, in conditions where cables are not exposed to heavier mechanical stress and tensile strain.
b. To avoid the effects of external impact, the adhering semi-conductive layer extruded between conductor and insulation, along with concentric copper conductor, secures restriction of electric field and resistance to partial discharges.
c. Due to its very low factor of dielectric loss, which remains constant over its entire operating lifetime, and owing to excellent insulation property of XLPE-material, firmly longitudinally spliced with inner and external screen of semi-conductive material (extruded in one process), the cable has a high operating reliability.
International: IEC 60502-2, IEC 60228
China: GB/T 12706.2-2008
Other standards such as BS,DIN and ICEA upon request
|MV(11kv 15kv 33kv) Power Cable|
|Model and Description Uo/U(Um)=3.6/6(7.2), 6/6(7.2), 6/10(12), 8.7/10(12), 8.7/15(17.5), 12/20(24), 18/30(36), 21/35(40.5), 26/35(40.5)kV||No.of Core||Conductor cross-section area(mm2)|
|xlpe insulation||1 core 3 core||10 16 25 35 70 95 120 150 185 240 300 400 500 630 sq mm|
|YJV, N2XSY;PVC sheathed power cable|
|YJV22;steel tape armoured,PVC sheathed power cable|
|YJV32,YJV42;steel wire armoured ,PVC sheathed power cable|
|YJLV, NA2XSY; PVC sheathed power cable|
|YJLV22;steel tape armoured,PVC sheathed power cable|
|YJLV32,YJLV42;steel wire armoured ,PVC sheathed power cable|
Packing & Shipping
All cable For exporting are well packed and protected by wooden drum or Wood and Steel Drum. The packing material is depended on the weight and size of cable. After the well packed cable drums sent to Sea Port, they are loaded into 20 FT container or 40 FT container. All cable drum are firmly fixed by safety belt to make sure, no movement during the sea freight. The size of the container is chosed according to weight of total loaded goods or as per the client's requirement.