|Place of Origin:||China|
Payment & Shipping Terms:
|Minimum Order Quantity:||200 Meters|
|Price:||US$0.42~150 / Meter|
|Packaging Details:||Wooden Drum|
|Delivery Time:||Depends on quantity|
|Payment Terms:||T/T, L/C|
|Supply Ability:||1500 KM per Month|
|Product Model:||LSZH Cable||Conductor Material:||Copper|
|Insulation Material:||XLPE||Cores:||3 Cores|
|Made Standard:||IEC60502-1||Working At:||90℃|
low smoke zero halogen wire,
lszh power cable
The metallic screen shall consist of either copper tapes or a concentric layer of copper wires or a combination of tapes and wires. The concentric conductor is applied directly over the inner covering. The metallic sheath consists of lead or lead alloy applied as a tightly fitting seamless tube. The metallic armor consists of either flat wire armor, round wire armor, and double tape armor.
Separation Sheath (for armored cable):
The separation sheath comprises a layer of extruded PVC, PE or LSZH applied over the laid up cores under the armor. PVC is normally of grade ST2 and PE of grade ST7. The nominal thickness is calculated by 0.02Du + 0.6mm
where Du is the fictitious diameter under the sheath in mm. For Electrical Cable without a lead sheath, the nominal separation sheath thickness shall not be less than 1.2mm. For Electrical Cable where the separation sheath is applied over the lead sheath, the nominal separation sheath thickness shall not be less than 1.0mm.
Lapped Bedding (for armored lead sheathed cable):
The lapped bedding applied to the lead sheath consists of either impregnated/synthetic compounded paper tapes or a combination of two layers of these paper tapes followed bya few layers of compounded fabulous materials. The thickness is around 1.5mm.
Armour (for armored cable):
The armor is applied over the inner covering helically. It consists of either flat galvanized steel wire armor (strip), round galvanized steel wire armor, and double steel tape armor.
Overall sheath comprises a layer of extruded either thermoplastic compound (PVC ST3 type or PE ST7 type or LSZH) or elastomeric compound (polychlorprene CSP or
chlorosulfonated PE). The nominal over sheath thickness is calculated by 0.035D+1 where D is the fictitiuous diameter immediately under the over sheath in mm. For unarmored Electrical Cable and Electrical Cable with the over sheath not applied over the armor, metallic screen or concentric conductor, the nominal over sheath thickness shall not be less than 1.4mm. And for Electrical Cable with over sheath applied over the armor, metallic screen or concentric conductor, the nominal over sheath thickness shall not be less than 1.8mm.
We are a manufacture in this filed for many years, we can offer our customers cables with good quality and price.
We Sincerely welcome customers at home and abroad to negotiate and cooperate with us !!!
Enter Your Message